Tigo offers one of two different AC Adapter Power Supply (PS) types with the management devices:
Wall Style Plug - 120/220 VAC household plug-in AC Adapter with barrel tip
DIN Rail Mount - 120/...
This article describes, step-by-step, how to change an MLPE serial number.
When a Tigo unit (maximizer, optimizer, other Tigo MLPE types) - or data logger (MMU, CC, or CCA) is replaced, its serial ...
How do I install the TS4?
The Installation Manuals for the TS4, CCA, TAP, RSS Transmitter, as well as Quick Start Guides, are located in the Technical Documentation section of our Downloads page:
There are many resources that are available to help you design and implement a successful system!
All of the Installation Manuals and Quick Start Guides can be found in the Technical Documentation ...
Full Deployment and System Discovery is required for all TS4-A-O systems, even though Optimization is functional with (or without) the Discovery process.
Blind Deployment is not recommended or sup...
This article discusses the installation of a PV-Off emergency stop to signal the MLPE to disconnect their panels from the strings. Tigo has called this PV-Safe and PV-Off. It is essentially the sam...
This article discusses the requirements for the data cable that connects the TAP (or Gateway), to the Data Logger (CCA, Cloud Connect or MMU).
TAP Communication Cable Requirements