Connect the Tigo data logger (Cloud Connect, Cloud Connect Advanced or Management Unit) to Kaco data wires in order to monitor your inverter data from the Tigo Asset Management software.
Follow the wiring model in the following illustration and table.
|Tigo MMU||Tigo Cloud Connect||Tigo CCA||Kaco Inverter|
Default comms settings for all units: Baud Rate: 9600, Data Bits: 8, Parity: None, Stop Bits: 1
Each inverter must be assigned a Modbus address, "1" for the first inverter, "2" for the second, and so on.
Once inverters are connected, contact Tigo Technical Support via email Support@tigoenergy.com or via phone:
Americas: +1.408.402.0802 ext. 2
Have your inverter ModBus address ready (if applicable), and list of parameters you wish to display, and our team will complete the setup so that you can view the inverter readings on your Tigo monitoring portal.